LIQUID ALKALINE BOIL-OUT TREATMENT
MIC 8352 is a Liquid Alkaline Boil-Out and Cleaner that is designed to be used in industrial or commercial equipment to remove oil residues, mill scale, grease, dirt and many other contaminants that are harmful to new equipment. Proper cleaning of new and existing systems is essential to maintain system efficiency and good operating conditions. MIC 8352 is a precise blend of alkaline cleaners, emulsifiers, and wetting agents designed to clean a variety of heat exchange and process equipment.
Typical systems cleaned with MIC 8352
- Heat Exchangers
- Cooling Towers
- Hot Water Systems
- Process Equipment
The recommended dosage for MIC 8352 is 2.0-4.0 gallons for each 1000 gallons of system water. Heavy duty application may require a slightly higher dosage but CAUTION should be used. Caution: MIC 8352 is not recommended for use on aluminum equipment surfaces.
MIC 8352 may be fed directly from the drum to the partially filled system. At least 50% of the system should be filled prior to adding the calculated amount of MIC 8352. For boiler systems, the steam valves must be closed during boil-out. After treatment is added, increase the temperature slowly and keep the system under slight pressure during the boil-out period. Open each blowdown valve every two (2) or three (3) hours to assure open lines. After the boil-out is completed, slowly cool the system, drain and completely flush with a high pressure hose. For cooling towers, chilled and heat exchange equipment, circulate system until equipment is clean. Periodic inspections are recommended.
Harmful if swallowed. Strong alkaline. Avoid contact with skin, eyes and clothing. In case of contact, immediately flush skin or eyes with plenty of water for at least 15 minutes and get medical attention.
|5 gallon pail||47 lbs.|
|15 gallon drum||141 lbs.|
|30 gallon drum||283 lbs.|
|55 gallon drum||518 lbs.|
Please contact a Mid South Representative for additional product information and pricing.